SlideShare utilise les cookies pour améliorer les fonctionnalités et les performances, et également pour vous montrer des publicités pertinentes. Si vous continuez à naviguer sur ce site, vous acceptez l’utilisation de cookies. Consultez nos Conditions d’utilisation et notre Politique de confidentialité.
SlideShare utilise les cookies pour améliorer les fonctionnalités et les performances, et également pour vous montrer des publicités pertinentes. Si vous continuez à naviguer sur ce site, vous acceptez l’utilisation de cookies. Consultez notre Politique de confidentialité et nos Conditions d’utilisation pour en savoir plus.
An Overview of Electrical Hazards
This chapter lists the typical personnel safety hazards in industry and more specifically the types of
electrical safety hazards. It illustrates the types of electrical accidents that generally take place in
an industry and explains the normal preventive measures.
• Course overview
• General hazards in industry
• Electrical hazards
• Electrical accidents and safety measures
It is often remarked that electricity is a good slave but a bad master. Improper use of
electricity or careless handling of electrical equipment leads to a number of avoidable
accidents (many of which can be fatal) every year, resulting in huge loss. Out of the various
hazards present in any work place, the most important are the electric shock hazard and the
arc flash hazard. This course is about the latter and will discuss the underlying reasons for
arc flash incidents and the steps necessary to mitigate the effects of such incidents. .
1.2 General hazards in industry
In any industrial facility several types of hazards exist. The hazards may be due to any of the
• Electrical equipment
• Mechanical equipment
• Fire or flames
• Hazardous/toxic materials
• Hot liquids/gases
• Cold liquids
• Explosive gases
• Corrosive liquids
We are mainly concerned with electrical hazards and will briefly discuss the various types of
electrical hazards below.
2 Arc Flash Protection
1.3 Electrical hazards
Hazards from electrical equipment can be any of the following:
• Electric shock and associated effects such as:
¾ Internal organ damage due to passage of electricity through body
¾ Burns on skin at point of contact
¾ Injuries by electric shock combined with fall
• Arc flash causing external burns and injuries by explosive expansion of air due
to the arc.
• Fall from heights
• Corrosive liquids used in electrical equipment
• Hazards resulting from explosive atmosphere
• Hazards due to high temperature
The main hazard from electrical equipment is, naturally, the danger from electric shock.
Electric shock can be a result of contact with live parts such as electrical conductors or with
parts of equipment which are not normally live (such as enclosures) but become life due to
failure of electrical insulation.
Electric shock is thus a result of the following conditions.
• Exposure to live parts (Direct contact)
• Exposure to parts that accidentally become live (Indirect contact)
• Potential difference between different points in the earth under certain conditions
The last named is similar to indirect contact except that it does not involve contact with any
electrical equipment (either a live part or enclosure). Electric shock or electrocution can
cause many problems in a human body. Electric current flowing through body results in
muscular contraction. If the current flows through heart muscles it can cause stoppage of
heart by a condition called fibrillation. Even if an electric shock is not fatal, it can cause
other problems such as internal organ damage due to excessive heating of body tissues, burns
at the point of contact of the skin with live conductors, loss of consciousness or loss of
balance resulting in fall while working at a height.
In some instances an electric shock may not by itself cause an injury, but a resulting fall
from a height can as described in a subsequent paragraph.
Apart from electric shocks caused by contact with parts that are (or become) live, another
major danger for those who work on electrical equipment is the hazard due to arc faults.
Such faults are often caused by the affected workers themselves, when they work on or in the
vicinity of live equipment and cause a short circuit fault inadvertently. In fact, arc faults in
equipment and their potential dangers are subjects of extensive study and have given rise to
standards such as IEEE 1584 (Guide for Performing Arc-Flash Hazard Calculations). This is
the principal subject matter of this course and will be discussed in detail later.
Arc flash can also result when safe clearances between a live part and earth are compromised
during work. This can result in the intervening air space breaking down and initiating an arc.
This is particularly true of exposed overhead equipment such as switchyards.
The most serious hazard of an arc flash is burn injuries resulting from the arc with the
seriousness of injury dependent on the following factors:
• Fault energy as given by the fault level of the system (VA)
• Time of fault clearance
For example, the arc energy in an MV system short circuit fault is usually much higher
An Overview of Electrical Hazards 3
compared to an LV mains circuit fault, which in turn has a much higher energy compared to
a branch circuit fault in the same system. The longer an arc fault is allowed to persist, higher
the damage. Faults, which are cleared much faster, are therefore much less dangerous from
viewpoint of injury.
High-energy faults will also cause melting of components such as copper/aluminum
conductors or steel parts of enclosure. Copper is particularly dangerous because it can result
in deposition of toxic copper salts on the skin. Internal injuries and also hearing damage can
result from the blast pressure and damage to eyes can happen as a result of the bright light of
the arc flash.
Sometimes, the sudden expansion of air due to an arc fault within an enclosed space may
dislodge mechanical parts such as terminal covers with a great force. Documented cases of
such accidents causing injury or even death are on record. It is common practice in design of
equipment such as HV switchgear to provide vents or flaps, which open in the event of
explosive arc faults thus avoiding damage to the enclosure. They also help to direct the arc
products way from an operator who may be stationed nearby. The newer versions of
switchgear are built to be arc resistant in which an internal arc is unlikely to cause injuries to
operating personnel in the vicinity and the energy is contained within the arc resistance
Fall from heights
A lot of maintenance work is carried out on overhead lines and outdoor switchyard
equipment at a height. Also maintenance work on large power transformers requires people
to work on the top of the tank. Work on lighting fixtures and wiring involves working at a
considerable height. A fall can badly inure the worker and can sometimes be fatal too. Often
a minor electric shock can result in a fatal fall. People working at heights need to take
appropriate harness and fall arrest gear in order to protect themselves from a fall. Climbing
equipment used for such work including ladders, scaffolding and fixed/mobile platforms
need to be maintained in good condition.
Hazards from corrosive liquids
Acids and alkalis are highly corrosive and can cause injuries of they come into contact with
skin. In electrical installations, battery electrolyte which is an acid such as sulphuric acid or
alkaline such as sodium hydroxide pose such hazards. The hazards in this case are:
• Burns/irritation due to contact with skin
• Loss of sight or serious injury of eyes
• Danger of ingestion causing internal injuries in food path
• Danger of inhalation (fumes) causing similar injury to lung tissue
Hazards from explosive gases
Explosion is a result of accidental ignition of explosive mixtures formed by combustible
gases or fumes with oxygen in air. The source of ignition is often electrical. The effects of
explosions are manifold and can include:
• Burns by fire accompanying explosion
• Injuries from flying objects following an explosion
• Damage to limbs/internal injuries by the pressure wave generated by an explosion
Prevention of hazards due to explosions is primarily through the following approach.
• Prevent formation of explosive mixtures
• Prevent ignition of explosive mixtures if formed
• Limit the effect of explosion if ignition does take place.
An example of such a hazard is a dc installation using lead acid batteries, particularly those
4 Arc Flash Protection
of flooded type. During the process of charging these batteries hydrogen is generated (due to
electrolysis of the water in the electrolyte) and can form an explosive mixture with air.
Temperature or thermal hazards
Temperature hazard results from the high temperature on the surface of electrical equipment
enclosures and current carrying parts. External surfaces of electrical equipment often attain
elevated temperature, an example being the enclosure of bus ducts which can often attain
surface temperatures of over 60 Deg C. Exposed conducting parts such as overhead line
conductors can attain even higher temperatures. For example, the bus bars in switchgear
often run at temperatures in excess of 100 Deg C. Electrical joints/mating surfaces can have
temperatures exceeding the conductor temperature. This is because of increased localized
resistance. Apart from causing less serious burn injuries (compared to arc flash), high surface
temperature can cause ignition if flammable vapors are present in the environment.
Electrical faults can also cause fire danger as discussed in an earlier section. Special care is
required when the electrical equipment itself contains flammable materials, examples being
oil circuit breakers and mineral oil cooled transformers. In some cases, a fire can result
because of combustible materials stored in the vicinity of electrical equipment. Cables and
wiring are often a cause of fires as a result of an insulation failure due to excessive loading.
Cables can also catch fire due to exposure to flames (as in the case of boilers and furnaces).
Mechanical hazards result from exposure to moving parts of electrical equipment such as
motors, generators, circuit breaker mechanism etc. Hazards can result whenever there is
some kind of stored energy involved and can include springs, compressed air and high
Table 1.1 below shows the safety hazards posed by electrical equipments commonly used in
electrical generation and distribution systems and substations.
Electrical hazards in different equipment
Type of equipment Hazards
Generation equipment Electric shock, arc flash, mechanical
Transformers Electric shock, arc flash, fire hazard, fall
Overhead Transmission/distribution lines Electric shock, arc flash, fall from heights
Cables Electric shock, arc flash, fire hazard
Bus ducts Electric shock, arc flash, thermal hazard,
fall from heights
Switchgear Electric shock, arc flash, thermal hazard,
fire hazard, mechanical hazard
Motive equipment Electric shock, arc flash, thermal hazard,
Heating equipment Electric shock, arc flash, thermal hazard
Lighting equipment Electric shock, arc flash, thermal hazard,
fall from heights
Uninterrupted power supplies with battery Electric shock, arc flash, hazards from
corrosive liquids and explosive gases
An Overview of Electrical Hazards 5
1.4 Electrical accidents and safety measures
We will briefly discuss in this section about why electrical accidents happen and how we can
avoid them. These points will be elaborated in subsequent chapters in further detail.
Electrical accidents happen mostly as a result of the following:
• Failure to isolate or inadequate or insecure isolation of live parts
• Poor maintenance and faulty equipment
• Insufficient information about the system being worked on
• Carelessness and lack of safety procedures
Isolating normally live equipment before starting any work on it can improve safety
substantially in any system. We must however bear in mind that there are certain kinds of
equipment where live work is possible and certain kinds of activities where work in the
vicinity of exposed live parts is unavoidable. But such work must be carried out according to
well laid safety procedures.
The other major cause of accidents is faulty equipment (which can include both poorly
designed or improperly operating equipment). Unless safety is built into the design of the
equipment, it can result in accidents and injury. Similarly, improperly maintained equipment
too can result in failures and thereby cause accidents. Insufficient knowledge of operating
personnel, lack of familiarity with equipment and system etc. too can result in unsafe
situations. Absence of proper operational safety procedures and violations of existing
procedures can both result in accidents.
The following are the general safety measures, which need to be adopted to reduce the
possibility of accidents in electrical equipment.
• Safe design/installation of plant and equipment as per applicable codes and
• Safe operating and maintenance practices established through documented
procedures and instructions
• Appropriate knowledge on the part of workers by proper training and certification
• Posting clear warning signs at points of hazard
• Use of equipment/sensors to warn incipient problems with automated hazard
• Proper periodic inspection and prompt repairs
• Use of personal safety equipment mandated in safety procedures
• Creating an organizational safety structure to handle safety issues, lapses and
• Create safety awareness among the workforce
We will discuss these measures in detail in the ensuing chapters.
Improper use of electricity or careless handling of electrical equipment leads to a number of
otherwise avoidable accidents. Electrical safety is a well-legislated subject and the various
acts and regulations enacted in each industrialized country lay a lot of stress on the
responsibility of both employers and employees in ensuring safe working conditions.
However, it must also be understood that safety is not simply a matter of taking precautions
in the workplace but has to start at the stage of equipment design.
In any industrial facility, several types of hazards exist. The hazards may be due to electrical,
mechanical and several other causes. Electrical hazards are mainly from electric shock, fall
as a result of an electric shock, burns due to arc flash and injuries by explosive expansion of
air due to the arc. High temperature on the surface of electrical equipment
enclosures/exposed conductors and electrical faults resulting in fire within electrical
6 Arc Flash Protection
equipment or nearby combustible materials are other safety hazards. Electrical equipment
installed in explosive environment needs special attention.
Failure to isolate or inadequate or insecure isolation of live parts is the major reason for of
accidents. Isolating normally live equipment properly from supply mains before starting any
work on it can improve safety substantially. Poor maintenance and faulty equipment,
insufficient information about the system being worked on and lack of safety procedures are
the other major reasons for electrical accidents.